FLEXIBLE 
FIXTURE 


BULLETIN No.2063_ Jf 


-CROUSE-HINDS COMPANY | 
|| SYRACUSE,N.Y,U.S.A. | 


AVERY LIBRARY 
UNAM Uni 


Factory—Fixture Hanger Installation 


FLEXIBLE 
FIXTURE 
HANGERS 


BULLETIN NO. 2063 
November 1, 1924 


a 


CROUSE-HINDS COMPANY 
SYRACUSE, N. Y., U.S. A. 
Sales Offices 
if NEW YORK BOSTON CHICAGO 
1 Philadelphia Detroit St. Louis et inneapolis 
i] ssa ‘ S 


Copyright, 1924, Crouse-Hinds Company, Syracuse, N. Y. 


TYPE UNJ—Condulet Fixture Joint 
For Pendent Fixtures. Always Hangs Plumb 


Type UNJ with Fixture and T Condulet 


Type UNJ Condulet fixture joint is for supporting 
suspension type fixtures and can be used in conjunction 
with Condulets. It is a universal joint, so that the fixture, 
even though mounted on an inclined surface, will always 
hang plumb. 

The flexibility of type UNJ also prevents breaking the 
fixture at the point of suspension, due to strains set up by 
the wind or by hitting the fixture with a stepladder or the 
like. 

The construction is such that the wires pass through the 
fixture joint, consequently no wires are exposed. 

Type UNJ fixture joint will allow the fixture to swing 
through an angle of 20 degrees in any direction from the 
perpendicular. 


4 


TYPE UNJ—Condulet Fixture Joint 


For Pendent Fixtures. 


Always Hangs Plumb 


Size in inches 


Catalog Number . 
Standard Package 


Weight Std. Package . 


List Price, each. 


Size in inches 


Catalog Number . . . 


Standard Package 


Weight Std. Package 


List Price, each. . 
Size in inches 


Catalog Number . 
Standard Package 


Weight Std. Package 
bilistePrice, each, “7s 


Type UNJ 


TYPE UNJ 


VY-¥t 


AO lbs. 
$ .65 


55 Ibs. 
$ .75 


; 1-147 


UNJ31 
25 


40 lbs. 
$ .90 


tMale threads given first. 
Special Assortment: Any assortment of 100 black en- 
ameled and galvanized type UNJ Condulet fixture joints 
will be considered a standard package, 


5 


UNJ1308 
50 


34-Yot 
UNJ21 
50 


1-34 
UN J32 
25 


40 lbs. 
$1.00 


3-¥at 


UN J2308 
50 


55 Ibs. 
$2.75 


1-34 
UNJ3308 
25 


FIXTURE HANGERS 


Cushion 
For Condulets of the Obround Series 


Type C Condulet with 
Cushion Fixture Hanger and Fixture 


Cushion fixture hangers for Obround Condulets provide 
a self-aligning, flexible cushioned suspension for electric 
fixtures with 36 or 14-inch stem. 

They allow the fixture a free swing of approximately 
20 degrees in any direction and are provided with means 
to prevent turning or twisting the fixture stem in such a 
manner as to injure the wires or connections. 

The flexibility of the suspension relieves the lamp from 
the effect of any lateral vibration, and the cushion spring 
relieves it from the effect of any vertical vibration in the 
building, absorbing all shocks that would otherwise be 
transmitted to the lamp. 

The nipple which takes the fixture stem is brass and is 
furnished with a set screw. The 14-inch nipple is restricted 
to 34-inch inside diameter at the neck and, therefore, does 
not take any larger wires than the 34-inch nipple will take. 


6 


FIXTURE HANGERS 


Cushion 
For Condulets of the Obround Series 


Obround Fixture Hanger 


For Fixtures with 34-Inch Stem 


Total Weight of Fixture 
Size of ;Condulete. ...2. 3:5 


214 to 314 Pounds 


Catalog Numbers, oant..ee 
Standard Package . . SO ee 
Weight St Package ARa 

List Price, each = ie 


Total Weight of Fixture 


314 to 5 Pounds 


Size of Condulet . 34, 

CatalogsNumbere. Jats) teen a 28k 

Brandard Package wea ft os Yee. 100 
25 lbs. 


Weight Standard aes : 


List Price, each $ .60 


For Fixtures with 14-Inch Stem 


Total Weight of Fixture 314 to 5 Pounds 


Size of Condulet . 3/4, 
Catalog Number . 216k 
Standard Package . . 100 
Weight Sindard Package . 25 lbs. 


List Price, each $ .70 


Condulets, pages 10 to 27, Condulet Catalog No. 2000, 
it 


FIXTURE HANGERS 
Type H—Cushion 
For Form 10 Condulets of the G-H Series 
Without Adjustable Bar. Always Hang Plumb 


Type G Condulet with - 
Cushion Fixture Hanger and VDA Condulet 


These cushion fixture hangers are provided with a 
spring which carries the weight of the fixture and absorbs 
any shocks due to vibration of the building or from other 
causes, thus adding materially to the life of the lamp fil- 
ament, especially in mills, factories, or similar places where 
much vibration occurs. This hanger also allows a free 
swing of 8 degrees in any direction, giving protection from 
accidental impact or lateral vibration. 

The cushion springs are partially compressed by the 
normal weight of the fixture, yet have further travel in 
which to absorb the vibration. 


8 


FIXTURE HANGERS 


Type H—Cushion 
For Form 10 Condulets of the G-H Series 
Without Adjustable Bar. Always Hang Plumb 


Type H 
(Broken-away View) 


For Fixtures with 34-Inch Stem 


Total Weight of Fixture 16 to 30 


Catalog Number . . . 
Standard Package . . 
Weight Std. Package . 
List Price, each. . 


Total Weight of Fixture 


‘Catalog Number . . . 
Standard Package . . 
Weight Std. Package . 
List Price, each. . : 


Condulets: G-H series, pages 48 and 49, Condulet 
Catalog No. 2000; Type VDA, Advance Sheet No. 26, 


9 


FIXTURE HANGERS 
Type GS 
For Condulets of the GS Series. Always Hang Plumb 


Type GSC Condulet with 
Cushion Fixture Hanger and Fixture 


Type GS fixture hangers are furnished in two styles: 
ball and cushion, and provide a flexible suspension for 
electric fixtures with 4% or %4-inch conduit stem. They 
are particularly pleasing in appearance and very substan- 
tial, being fastened to the Condulet body by four 12-24 
round head brass screws. They are provided with means 
to prevent turning or twisting the fixture stem in such a 
manner as to injure the wires or connections. The ball 
hanger takes fixtures with %-inch conduit stem and will 
allow a free swing of 11 degrees in any direction. The 
cushion hanger takes fixtures with 34-inch conduit stem and 
will allow a free swing of 20 degrees in any direction. 

Both styles are similar in construction except that the 
cushion fixture hanger is provided with a spring which 
carries the weight of the fixture and absorbs any shocks 
due to vibration or other causes. Type GS ball fixture 
hanger is especially suitable for use in creameries and like 
places where the walls and ceilings are flushed down with 
a hose. It is absolutely watershedding and water cannot 
work into the conduit system or fixture stem. __ 


10 


FIXTURE HANGERS 
Type GS 
For Condulets of the GS Series. Always Hang Plumb 


Ball Fixture Hanger Cushion Fixture Hanger 
(Broken-away View) (Broken-away View) 


TYPE GS BALL HANGER 
For Form 5 Condulets 


For Fixtures with 14-Inch Stem 


GA PALO UIMDCL os ify ee ities cle eet yes 1 GOOD 
Standard Package . i ees aoe) oO 
Weight Standard Package: ts oe eA OUFLOS, 
List Price, each : . . RETIRES EA, SP id Be) ana 


TYPE GS CUSHION HANGER 
For Form 20 Condulets 


Size Ol. @ ONGUIt Stel mats ay gf. cene by. | ee 4-lnch: 
OLalNY Che DtcOle biKtUre -aeehy oe Geka oe yo eOOTCOrGU 
Cat alogaNUmMberees Hine Se a ele Teantn > a a ao4F 
Standard Package . . eee PAR Een pee) 
Weight Standard Package . ey eet, ome Fs fa WO) LS: 
List Price, each . . . Rieee th tw ye ee gad 


Condulets, pages 69 to 80, Condulet Catalog No. 2000. 
11 


FIXTURE HANGERS 
Type ARB 
For 4-Inch Outlet Boxes. Always Hang Plumb 


Cushion Fixture Hanger with 4-Inch Outlet 
Box and Fixture 


Type ARB fixture hangers are furnished in two styles: 
ball and fixture, and provide a flexible suspension for 
electric fixtures with % or 14-inch conduit stem. They 
are substantial and pleasing in appearance. 

The ball hangers are arranged with a ball-and-socket 
joint that permits a free swing of 11 degrees in any direc- 
tion. The cushion hangers are provided with a spring 
which carries the weight of the fixture and absorbs any 
shocks due to vibration or other-causes, and permits a free 
swing of 20 degrees in any direction. In both styles means 
are provided to prevent turning or twisting the fixture stem 
in such a manner as to injure the wires or connections. 

Fastening screws spaced 3! inches center to center are 
provided for use on standard 4-inch outlet boxes. 


12 


FIXTURE HANGERS 
Type ARB 
For 4-Inch Outlet Boxes. Always Hang Plumb 


Ball Fixture Hanger Cushion Fixture Hanger 
(Broken-away View) (Broken-away View) 


TYPE ARB BALL HANGERS 


Size of Conduit Stem . 


Catalog Number . ARB6 
Standard Package . . 25 

Weight Standard Package 50 Ibs 
List Price, each : $1.00 


TYPE ARB CUSHION HANGERS 


For Fixtures with 34-Inch Stem 


Total Weight of Fixture 16 to 30 


Catalog Number . . . | ARB7 ARB9Y ARB11 
Standard Package . . | 25 25 25 
Weight Std. Package . | 50 lbs. 50 Ibs. 60 Ibs 


List Price, each. . . . | $1.00 


Total Weight of Fixture 


Catalog Number . 
Standard Package 
Weight Std. Package . 
List Price, each. . . . 


TYPE ALC—Condulet Fixture Joint 
For Pendent Fixtures. Always Hangs Plumb 


Type ALC with Fixture 


Type ALC Condulet fixture joint is for supporting 
suspension type fixtures with 44-inch conduit stem. The 
fixtures are suspended from a univer sal joint which assures 
that the fixture will hang plumb. It also prevents breaking 
the fixture stem at the point of suspension, due to strains 
set up by the wind or by hitting the fixture with a step- 
ladder or the like. 

This universal joint permits the fixture to swing through 
an angle of about 20 degrees in any direction from the 
perpendicular. 

To remove a fixture it is necessary only to take off the 
cover of the Condulet, disconnect the fixture wires and 
slide the supporting nipple out of the groove in the Con- 
dulet, thus removing the entire fixture as a unit. 

The back of type ALC conforms to the shape of the 
conduit, therefore, it can be mounted close to the ceiling 
even though the ceiling is inclined. It can also be used 
close to the roof when the roof is flat or inclined at practi- 
cally any angle. This feature is especially valuable for 
use with roofs of saw-tooth construction. 

The cover is fastened to type ALC with one screw. 
The fixture stem cannot turn or twist in the joint in such 
a manner to injure the wires or connections. 


14 


TYPE ALC—Condulet Fixture Joint 
For Pendent Fixtures. Always Hangs Plumb 


Type ALC 
TYPE ALC 
For Fixture with 14-Inch Stem 


Size in inches 


Catalog Number . ALC2 
Standard Package . . 25 
Weight Se dsel Package . 70 Ibs. 
List “Price, each ; $ .85 


TYPE AOC—Condulet Fixture Joint 
For Pendent Fixtures. Always Hangs Plumb 


Type AOC 
Type AOC Condulet fixture joint fulfills the same 
purpose as type ALC, described on the opposite page, but 
the Condulet body is of the Obround shape and is provided 
with a cover fastened on with a wedge nut. 


TYPE AOC—For Fixtures with 14-Inch Stem 


PImeriimiicnes; sae a asf, tee, yy, 

Catalog Numbers... .o. 2 e-|"AOCI 
Standard Package . Poa te eel tOU 

Weight eel Package Sea GorlOs: 

List Price, each . . Coe a esas LO : 


15 


COVER—With Cord Clamp 
For Condulets of the Obround Series 


Type C Condulet with 
Cover with Cord Clamp, and Cord 


Drop cord fixtures, especially in industrial plants, are 
frequently subject to very hard usage. The Condulet 
cover with cord clamp, shown on this page, acts as a 
safeguard for the upper end of such drop cords, and 
prevents putting any strain on the soldered connections 
of the conductors. The hole through the cover is provided 
with a bushing. 

This cover fits any Condulet of the Obround series in 
the sizes listed. 


Size in inches 


Catalog Number . 
Standard Package . : 
Weight Standard Package ' 
List Price, each 


AVERY LHBRARY 


